Clean Audio for TV broadcast: An Object-Based Approach for Hearing-Impaired Viewers - April 2015
Audibility of a CD-Standard A/DA/A Loop Inserted into High-Resolution Audio Playback - September 2007
Sound Board: Food for Thought, Aesthetics in Orchestra Recording - April 2015
Using Active Noise Control for Recording Studio HVAC System Silencing
DSP technology is now being used for active noise control systems. When applied to building HVAC systems, active noise control can reduce low-frequency noise from the airhandler. An infinite impulse response (IIR) adaptive filter approach enables the controller to compensate for acoustic feedback from the loudspeaker to an upstream input microphone, allowing the system to cancel random, broadband noise. These systems, in active/passive hybrid form, have been applied to recording studio installations to achieve background levels approaching NC 15.
Click to purchase paper or login as an AES member. If your company or school subscribes to the E-Library then switch to the institutional version. If you are not an AES member and would like to subscribe to the E-Library then Join the AES!
This paper costs $20 for non-members, $5 for AES members and is free for E-Library subscribers.